OFF GRID LIVING – 1. How to install a tiny wood stove in a shed.
OFF GRID LIVING – 1. Installing a small woodstove in a shed or tiny home with a metal roof.
To install your wood burner in your shed you will need a hearth, some shielding, a flue kit and a few tools. ( and a stove!)
- Tools – The tools required to do the job
- Hearth – Size, thickness & fixings.
- Shielding – Safe distances from combustibles, fixings
- Flue kit – Flue component list and tolerances
- The stove.
- Safety – CO alarm & ventilation.
Drill, jigsaw, spirit level, screw driver, 10mm drill, 4mm drill, cartridge gun, knife, marker pen, extension lead, step ladder
Installing your small woodstove in a shed is a freestanding scenario and therefore requires different hearth arrangements that if it was being fitted into a fireplace recess. If your stove is independently certified not to heat the hearth underneath it to more than 100 degrees centigrade ( check manufacturer stove details), then the hearth regulations are very simple as a full thickness constructional hearth is not required:
For s shed stove install the hearth needs to be a minimum 12mm thick and of non-combustible material. (e.g. tiled floor surface or glass laid onto carpet/wood floor etc.).
In this case the hearth must be a minimum size: 840mm x 840mm. There must also be a minimum 150mm of hearth at each side and rear of the stove and a minimum 225mm in front of the stove door (300mm if the stove is designed to burn with doors open)
Summary; 12mm thick, 225mm to front & 150mm to sides.
- Do I need a hearth if I have a stone floor?
Answer. YES. The hearth must provide a “visually apparent warning” (see Approved Document J 2.26).
This prevents you just simply placing your stove onto a solid floor such as a tiled kitchen floor for example without any discernable visible edge.
We used a glass plate. (It was undersized as only 700 x 600 but the stove is very small and with this size we were able to maintain the 150 mm to each side and 250mm to the front.
(The most important reason for the provision of a hearth is to guard against the potential resulting problems in the event of a hot ember falling out of the stove when the door is opened so the frontal hearth requirement is the most important one to adhere to.)
How close can the stove go to the wall of my shed?
In order to position the stove and/or flue closer to combustible materials then they can be shielded using insulative board.
Safe distance of 200mm when shielding combustibles with a 25mm thick board with a 15mm air gap behind.
Does the flue pipe need shielding?
Single wall flue pipe must be 3X diameter from combustibles. To a shielded combustible surface the safe distance can be reduced depending on the amount of shielding used.
Twin wall pipe must be 50mm from combustibles
The flue kit installed in this instance is a mixture of single skin flue pipe and twin wall flue pipe. Made in the UK this is the highest quality British made flue money can buy. A combination of VITRELUX and HT-S it is a system designed to provide an effective draw on a system of approx. 3.6m high. The flue size increases from 100mm diameter to 125mm diameter and an A?D Swedish cowl have also been utilised to negate the relatively short flue height.
This ‘SHED FLUE KIT’ comprises of the following components;
1 x 1000mm with door MIDTHERM VITRELUX SINGLE WALL FLUE PIPE.
1 x 45 elbow MIDTHERM VITRELUX SINGLE WALL FLUE PIPE.
1 x 45 elbow with door MIDTHERM VITRELUX SINGLE WALL FLUE PIPE.
2 x stainless steel joint clips MIDTHERM VITRELUX SINGLE WALL FLUE PIPE.
1 x adaptor 100mm single wall flue to 125mm twin wall flue MIDTHERM HT-S TWIN WALL FLUE PIPE
1 x wall band support bracket MIDTHERM HT-S TWIN WALL FLUE PIPE
1 x 500 mm length of 15mm fire rope. MIDTHERM HT-S TWIN WALL FLUE PIPE
1 x 500 mm MIDTHERM HT-S TWIN WALL FLUE PIPE (stainless finish)
1 x 500 mm MIDTHERM HT-S TWIN WALL FLUE PIPE (black finish)
1 x Storm collar MIDTHERM HT-S TWIN WALL FLUE PIPE (black finish)
1 x Swedish A/D cowl MIDTHERM HT-S TWIN WALL FLUE PIPE (black finish)
1 x Silicone flashing
1 x Silicone flashing fixing kit
1 x cartridge heatproof adhesive
1 x cartridge heatproof silicone
1 x cartridge fire cement
The cost of this exact shed flue kit with the additional black powder coating is £585.
Small stoves are the best choice for small spaces such as sheds. If you install a stove that is too large then you will never be able to run it properly and you will quickly soot up the flue. Choose a small stove that has a small footprint to maximise the small space you have. You may want to consider having an additional back boiler for supplying hot water or to run a small radiator if your shed has been partitioned and has separate internal areas.
The Hobbit stove with stand is what we suggest is the best ‘shed stove’ to install and will heat a 20′ x 10′ shed no problem.
Safety & Ventilation
Installing a CO and smoke alarm in the shed is essential for the safety of everyone inside especially if the shed is very air tight.
Good ventilation is also essential and installing an air vent is always a good idea to insure the stove has a good supply of air.
If you are intending to sleep in the shed then you must install the stove in accordance with the current regulations.
Download the regulations for fitting stoves for free.
Another very helpful guide to assist you in understanding the requirements of Approved doc. J is BS 8511:2010. There is a helpful graphic which can be viewed at the link below.
HOW TO INSTALL YOUR TINY WOODSTOVE.
The hearth needs to be secured on some pads of carpet, adhesive or sand or a stiff mortar. Once the hearth has been positioned the stove can be positioned and the centre point for the flue found by using a plumb line or spirit level.
Attach the shielding using the heat proof adhesive and a couple of screws to hold it in position until the adhesive cures.
Here is a guide to the typical shielding that will be required.
Mark the edge of the hole and drill with a 10mm drill and then cut out the hole using a jigsaw.
Attach the wall band support bracket in position ready to accept the fist 500mm length of twin wall flue pipe. Firstly attach the single to twin adaptor to this length. You can assemble the single skin flue parts and offer everything up to make sure you position the twin wall at the correct height.
Cut the silicone flashing and then attach to the roof. Seal everything using the heatproof silicone. The upcoming video will help you identify all of thee places and details the installing of the silicone boot flashing.
Attach second black 500mm length with the Swedish cowl already attached.
Attach the storm collar
Assemble the single wall parts and join each with a seal of fire cement and use a joint clip between each part also.
Attach the trim plate or fill the visible void with the length of fire rope.
Light your stove to test all is properly connected.
This video shows you how to install a silicone flashing onto a metal corrugated roof